Thanks for the help. How would I know if the white wire is neutral in the 2-way switch box, or if it's to loop power back up to the light? The main power comes into the 2-way switch box, I've hooked a pigtailed power(black) to the 2-way switch, then there's a 14-2 line running to the light (white/black) The white and black are hooked to the light fixture as normal. The white wires in the 2-way switch box are all together. (Coming in, going to the light for 2-way switch, and going to the light for the 3-way switch.