The light requires 5 60W light bulbs and replaced a single bulb hanging light. The dimmer switch is rated for 600W
There is an extra black wire left capped/unused in the ceiling box that I think may be the problem.
The dimmer switch seems to be connected ok according to my limited expertise?
If I change the connection in the ceiling box - ie. connect the unused wire instead of the red wire, what damage could occur?