Hmm. I did check the breaker at the panel and it has a black wire going to the breaker, which i think is right. Now what i did also see is the common bar has all white wires going to it But also the ground wire is connected to it as well. I dont think that should be there, It should be connected to a seperate bar were all the grounds go to, right? well i'll have to find out if anything else is on that line. And i will put a GFI plug in the first outlet. Thanks again.