Chris, as long as your electrial system is grounded, I don't see why you would need an additional ground rod. Code would require an additional rod to be connected into your exiting gounding electrode system anyway. The manuf. may just be assuming the worst case i.e. an ungrounded system. You might want to check with the manuf's customer service dept. just to be sure.