Well, I'm remodeling an old 60's bathroom. I need to install a GFCI. The circuit in the bathroom also feeds two other rooms. I only really need to protect the bathroom part of the circuit with the switch but the neutrals are all pigtailed. Everytime I connect the rest of the neutral lines to the GFCI and feed neutrals, the GFCI trips.