Right after the Thermostat cycles the Furnace Off, the fan starts back up for a second or two, shuts off, then repeats this two more times. Is this normal? Or is this pulsing of the fan motor going to cause additional wear on the fan motor contactor, etc.?
Day & Night (BDP Company, Div. of Carrier)